The ultraviolet sterilizer is installed indoors horizontally, and the bracket is fixed on the designated foundation or workbench. (Connected to the water inlet E and the water outlet G) the position of the sterilizing device in the room, in addition to considering the convenience of water supply and drainage, and meeting the requirements of the process flow, also Pay attention to leave an installation position to extract the ultraviolet lamp tube and space, the electric control box is installed near the device, the relative humidity of the environment is not greater than 80 ℃, no corrosive gas, no conductive dust, no strong vibration and shock. 1. Installation: This product is of pipeline type, and one of the two water outlets can be selected as the water inlet and the other as the water outlet according to the direction of the pipeline. It can be placed horizontally or vertically according to the needs of the user. In order to facilitate the replacement of the lamp tube and the side of the quartz tube To leave a space of 1.2m. After the product is installed, conduct a water test first to ensure that there is no water leakage, then turn on the power, and after confirming that the light tube is on for 3-5 minutes, (as shown in Figure 1) turn on the water inlet valve and the water outlet valve, and then the machine starts to run.
2. Maintenance of ultraviolet sterilizer: 1. Disassembly of quartz tube: first turn off the power, open the cover on both sides of the sterilizer, take out the lamp tube, remove the glands at both ends, and take out the "O" rubber ring in the water seal seat , and then slowly pull out the quartz tube. 2. Assembly of the quartz tube: The operator should not directly touch the surface of the quartz tube with hands, so as not to be dirty and affect the transparency. Align the quartz tube with the water-sealed holes at both ends, insert the quartz tube, and the margin at both ends should be equal. "O" type rubber ring, tighten the gland slowly and evenly, and the force should not be too large, so as not to cause the quartz tube to break, and then conduct a water test, if there is water leakage, gently tighten the gland until there is no water leakage, and finally install it The lamp is ready to operate. 3. Precautions for the ultraviolet sterilizer: 1. Before running through the water, check that there is no water leakage at both ends, and there must be no water drops on the inner wall of the quartz tube.
2. The lamp corner socket should be inserted according to the number or color. 3. Ground protection. 4. Avoid direct exposure of ultraviolet rays to the human body.
5. Do not install the sterilizer in a place that is too humid or where there is a lot of shock and vibration. High humidity can easily cause damage to electrical components, and excessive shock and vibration can cause damage to lamp tubes and quartz tubes. 6. The quartz tube should be scrubbed regularly, and alcohol should be used as the scrubbing solution when scrubbing. Poolking is the best swimming pool equipment manufacturer and supplier in China. Poolking exists to provide the highest quality swimming pool equipment while offering competitive pricing..